Learn about the temperature and how start-stop shortens the life of a starter battery.
Heat is a killer of all batteries and high temperatures cannot always be avoided. This is the case with a battery inside a laptop, a starter battery under the hood of a car and stationary batteries in a tin shelter under the hot sun. As a guideline, each 8°C (15°F) raise in temperature cuts the life of a sealed lead acid battery in half. A VRLA battery for stationary applications that will last 10 years at 25°C (77°F) would only live five years if operated at 33°C (92°F). The same battery would cease after 2½ years if kept at a constant desert temperature of 41°C (106°F). Once the battery is damaged by heat, the capacity cannot be restored.
The life of a battery also depends on the activity and is shortened if the battery is stressed with frequent discharge. According to the 2010 BCI Failure Mode Study, starter batteries have become more heat-resistant. In the 2000 study, a temperature raise of 7°C (12°F) affected battery life by roughly one year; in 2010 the heat tolerance has been widened to 12°C (22°F). Other statistics reveal that in 1962, a starter battery lasted 34 months; in 2000 the life expectancy had been increased to 41 months. In 2010, BCI reports an average age of 55 months cranking vehicle engines of which the cooler North attains 59 months and the warmer South 47 months. Colloquial evidence in 2015 reveals that a battery kept in the trunk of a car lasts one year longer than if positioned in the hot engine compartment.
Cranking the engine poses minimal stress on a starter battery. This changes in a start-stop function of a micro hybrid. The micro hybrid turns the IC engine off at a red traffic light and restarts it when the traffic flows. This results in about 2,000 micro cycles per year. Data obtained from car manufacturers show a capacity drop to about 60 percent after two years of use in this configuration. To solve the problem, automakers are using specialty AGM and other variations that are more robust than the regular lead acid. [BU-211, Alternate Battery Systems]
Figure 1 shows a capacity drop from 100 percent to about 50 percent after the battery had been exposed to 700 micro cycles. The simulated start-stop test was performed in Cadex laboratories. CCA remains high and only shows a decline after about 2,000 cycles.
Courtesy of Cadex, 2010
Test method: The test battery was fully charged and then discharged to 70 percent to resemble the SoC of a micro hybrid in real life. The battery was then discharged at 25A for 40 seconds to simulate engine off condition at stoplight with the headlight on, before cranking the engine at 400A and recharging. The CCA readings were taken with the Spectro CA-12.
The cell voltages on a battery string must be similar, and this is especially important for higher-voltage VRLA batteries. With time, individual cells fall out of line; applying an equalizing charge every six months or so should theoretically bring the cells back to similar voltage levels. While equalizing will boost the needy cells, the healthy cell gets stressed if the equalizing charge is applied carelessly. (See BU-404: Equalizing Charge)
What makes this service so difficult is the inability to accurately measure the condition of each cell and provide the right dose of remedy. Gel and AGM batteries have lower overcharge acceptance than the flooded version and different equalizing conditions apply. Deteriorating cell balance is related to aging and any attempt to re-balance will not correct the condition but provide a Band Aid solution to extend battery life. Always refer to the manufacturer’s specifications.
Water permeation, or loss of electrolyte, is a concern with sealed lead acid batteries, and overcharging contributes to this condition. While flooded systems accept water, a fill-up is not possible with VRLA. Adding water has been tried, but this does not offer a reliable fix. Experimenting with watering will turn the VRLA into unreliable battery that needs high maintenance.
Flooded lead acid batteries are one of the most reliable systems. With good maintenance these batteries last up to 20 years. The disadvantages are the need for watering and providing good ventilation.
When VRLA was introduced in the 1980s, manufacturers claimed similar life expectancy to the flooded systems, and the telecom industry was enticed to switch to these maintenance-free batteries. By mid-1990 it became apparent that the life for VRLA did not replicate that of a flooded type; the useful service life was limited to only 5–10 years. It was furthermore noticed that exposing the batteries to temperatures above 40°C (104°F) could cause a thermal runaway condition due to dry-out condition.
A new lead acid battery should have an open circuit voltage of 2.125V/cell. This indicates a fully charged battery. During buyer acceptance, the lead acid may drop to 2.120V. Shipping, dealer storage and installation will decrease the voltage further in idle mode, but the battery should never go much below 2.10V/cell as this could cause sulfation. Battery type, applying a charge or discharge within 24 hours before taking a voltage measurement, as well as temperature will affect the voltage reading. A lower temperature lowers the OCV; warm ambient raises it.
Last updated 2015-04-29
Comments are intended for "commenting," an open discussion amongst site visitors. Battery University monitors the comments and understands the importance of expressing perspectives and opinions in a shared forum. However, all communication must be done with the use of appropriate language and the avoidance of spam and discrimination.
If you have a question, require further information, have a suggestion or would like to report an error, use the "contact us" form or email us at: firstname.lastname@example.org. While we make all efforts to answer your questions accurately, we cannot guarantee results. Neither can we take responsibility for any damages or injuries that may result as a consequence of the information provided. Please accept our advice as a free public support rather than an engineering or professional service.